A solids-free sewer is a network of small-diameter pipes that transports pre-treated and solids-free wastewater (such as Septic Tank effluent). It can be installed at a shallow depth and does not require a minimum wastewater flow or slope to function.
Solids-free sewers are also referred to as settled, smallbore, variable-grade gravity, or septic tank effluent gravity sewers. A precondition for solids-free sewers is efficient primary treatment at the household level. An interceptor, typically a single-chamber Septic Tank (S.9), captures settleable particles that could clog small pipes. The solids interceptor also functions to attenuate peak discharges. Because there is little risk of depositions and clogging, solids-free sewers do not have to be self-cleansing, i.e., no minimum flow velocity or tractive tension is needed. They require few inspection points, can have inflective gradients (i.e., negative slopes) and follow the topography. When the sewer roughly follows the ground contours, the flow is allowed to vary between open channel and pressure (full-bore) flow.
If the interceptors are correctly designed and operated, this type of sewer does not require self-cleansing velocities or minimum slopes. Even inflective gradients are possible, as long as the downstream end of the sewer is lower than the upstream end. In sections where there is pressure flow, the water level in any interceptor tank must be higher than the hydraulic head within the sewer, otherwise the liquid will flow back into the tank. At high points in sections with pressure flow, the pipes must be ventilated.
Solids-free sewers do not have to be installed on a uniform gradient with a straight alignment between inspection points. The alignment may curve to avoid obstacles, allowing for greater construction tolerance. A minimum diameter of 75 mm is required to facilitate cleaning. Expensive manholes are not needed because access for mechanical cleaning equipment is not necessary. Cleanouts or flushing points are sufficient and are installed at upstream ends, high points, intersections, or major changes in direction or pipe size. Compared to manholes, cleanouts can be more tightly sealed to prevent stormwater from entering.
Stormwater must be excluded as it could exceed pipe capacity and lead to blockages due to grit depositions. Ideally, there should not be any storm- and groundwater in the sewers, but, in practice, some imperfectly sealed pipe joints must be expected. Estimates of groundwater infiltration and stormwater inflow must, therefore, be made when designing the system. The use of PVC pipes can minimize the risk of leakages.
| - Does not require a minimum gradient or flow velocity
- Can be used where water supply is limited
| - Space for interceptors is required |
- Interceptors require regular desludging to prevent clogging
This type of sewer is best suited to medium-density (peri-)urban areas and less appropriate in low-density or rural settings. It is most appropriate where there is no space for a Leach Field (D.8), or where effluents cannot otherwise be disposed of onsite (e.g., due to low infiltration capacity or high groundwater). It is also suitable where there is undulating terrain or rocky soil. A solids-free sewer can be connected to existing Septic Tanks where infiltration is no longer appropriate (e.g., due to increased housing density and/or water use).
As opposed to a Simplified Sewer (C.4) a solids-free sewer can also be used where domestic water consumption is limited. This technology is a flexible option that can be easily extended as the population grows. Because of shallow excavations and the use of fewer materials, it can be built at considerably lower cost than a Conventional Sewer (C.6).
If well constructed and maintained, sewers are a safe and hygienic means of transporting wastewater. Users must be well trained regarding the health risks associated with removing blockages and maintaining interceptor tanks.
Operation & Maintenance
Trained and responsible users are essential to avoid clogging by trash and other solids. Regular desludging of the Septic Tanks is critical to ensure optimal performance of the sewer. Periodic flushing of the pipes is recommended to insure against blockages. Special precautions should be taken to prevent illegal connections, since it is likely that interceptors would not be installed and solids would enter the system. The sewerage authority, a private contractor or users committee should be responsible for the management of the system, particularly, to ensure that the interceptors are regularly de-sludged and to prevent illegal connections.
Solids-Free Sewers are good upgrading options for Leach Fields that have become clogged and/or saturated with time as well as for rapidly growing areas that would not accommodate more Septic Tanks with Leach Fields.
- Azevedo Netto, J. and Reid, R. (1992). Innovative and Low- Cost Technologies Utilized in Sewerage. Technical Series No. 29, Environmental Health Program, Pan American Health Organization, Washington, D.C., US. (A short summary and component diagrams – Chapter 5)
- Crites, R. and Tchobanoglous, G. (1998). Small and Decentralized Wastewater Management Systems. WCB/McGraw- Hill, New York, US. pp. 355-364. (Book; A short summary of design and construction considerations)
- Mara, D. D. (1996a). Low-Cost Sewerage. Wiley, Chichester, UK. (Assessment of different low-cost systems and case studies)
- Mara, D. D. (1996b). Low-Cost Urban Sanitation. Wiley, Chichester, UK. pp. 93-108. (Book; Comprehensive summary including design examples)
- Otis, R. J. and Mara, D. D. (1985). The Design of Small Bore Sewer Systems. UNDP Interregional Project INT/81/047, The World Bank and UNDP, Washington, D.C., US. (Comprehensive summary of design, installation and maintenance)
The material on this page was adapted from:
Elizabeth Tilley, Lukas Ulrich, Christoph Lüthi, Philippe Reymond and Christian Zurbrügg (2014). Compendium of Sanitation Systems and Technologies, published by Sandec, the Department of Water and Sanitation in Developing Countries of Eawag, the Swiss Federal Institute of Aquatic Science and Technology, Dübendorf, Switzerland.
The 2nd edition publication is available in English. French and Spanish are yet to come.